Mit dem NL120 kann ein Datenlogger über ein lokales Netzwerk oder eine Internetverbindung über TCP/IP kommunizieren. Das kleine Modul wird direkt auf den 40-Pin Port am CR1000 oder CR3000 aufgesteckt.Lesen Sie mehr
The NL120 uses a straight through cable when the cable is run from a hub to the NL120. A 10baseT Ethernet crossover cable is used if the cable is run directly from the computer to the NL120. For cable lengths longer than 9 feet, either a shielded 10baseT Ethernet cable or the 28033 surge protector needs to be used.
The NL120 is set up using the Device Configuration utility (DevConfig). DevConfig is bundled with our PC400, RTDAQ, and LoggerNet software and is available, at no charge, from: www.campbellsci.com/downloads
|Power Requirements||12 V (supplied through the data logger’s peripheral port)|
|Ethernet Speed||10Base-T (10 Mbps), half-duplex|
|Typical Current Drain||20 mA|
|Dimensions||10.2 x 6.4 x 2.8 cm (4.0 x 2.5 x 1.1 in.)|
|Weight||66.62 g (2.35 oz)|
EMI and ESD Protection
|European Standards||Meets requirements for a class A device under European Standards.|
|Application of Council Directive(s)||89/336/EEC as amended by 89/336/EEC and 93/68/EEC|
|Standards to Which Conformity Is Declared||EN55022-1; 1995 and EN50082-1: 1992|
|LoggerNet||Version 3.2 or later|
|PC400||Version 1.3 or later|
|DevConfig||Version 1.5 or later|
Please note: The following shows notable compatibility information. It is not a comprehensive list of all compatible products.
|ENC12/14||Attached to a CR1000|
|ENC14/16||Attached to a CR1000 or CR3000|
|ENC16/18||Attached to a CR1000 or CR3000|
A 10baseT Ethernet straight through cable is used when the cable is run from a hub to the NL120. A 10baseT Ethernet crossover cable is used if the cable is run directly from the computer to the NL120. For cable length longer than 9 ft, the 10baseT Ethernet cable must be shielded or the 28033 surge suppressor must be used.
The NL120 fastens onto the data logger's 40-pin peripheral port. This means that the NL120 is only compatible with the CR1000 and CR3000. It is NOT compatible with the CR800, CR850, CR200X, CR5000, or CR9000X dataloggers.
Number of FAQs related to NL120: 23
Alle anzeigenWenige anzeigen
The NL120 is a communications peripheral only. It does not provide additional analog terminals for a datalogger.
Yes. The NL120 operates as transparent.
Yes, the NL120 can be repaired. Refer to the Repair and Calibration page for the process of returning equipment to Campbell Scientific.
The PakBus protocol allows multiple simultaneous connections. The PakBus address that LoggerNet uses for itself on one of the PCs needs to be changed, though.
The following are some possible causes:
No. Configurations can be changed, however, via any other mode of communication with the datalogger.
Yes. By configuring the NL120 as a CSDC device, both the NL120 and COM320 can share the same CS I/O port. The CR1000 and CR3000 are capable of multi-threading, so the NL120 and COM320 can run in parallel. For more information, refer to the NL120 Ethernet Module Instruction Manual.